- Design and functional solution
- Starting fire detection
- Serviceability check and service
Key product features
It is mainly used to detect the onset of fire locally.
When smoke detectors that signal a fire, they instruct the AOP Control Unit to lower the fire shutter.
Local detection consists of a system of autonomous detectors, one of which is the Smoke Detector. The number of smoke detectors depends on the width of the shutter. The EN standard states 1 smoke detector on each side of the shutter for shutters up to 4 meters clear width and 2 smoke detectors on each side of the shutter for shutters wider than 4 m.
Additional equipment of the AVAPS fire shutter. In case of connection only to local fire detection, it is a mandatory accessory of the fire shutter.
- Identification of smoke, and therefore fire, at the beginning
- Communication with the fire shutter control unit closes the fire dividing structure and prevents the occurrence of fire in other parts of the building.
Materials for download
Are you interested in this product?
Contact us using the form or call us.
We develop, sell, manufacture, assemble, service our products ourselves and at the same time we also offer our professional services to external customers.